ORIFICE ASSEMBLY AND HOSE REPLACEMENT (Sheet 2 of 3)
Pull breakaway socket (A) from orifice assembly (B).
Using screwdriver, loosen hose clamps (C)
and (D) by prying tab (E) up.
Remove breakaway socket (A) from hose (F).
Remove hose (F) from heater.
Using retaining ring pliers, remove snap ring (G).
Remove orifice assembly (H) from bracket (J).
CLEANING AND INSPECTION:
Clean hose and orifice connector with warm
water and liquid detergent (Item 33, Appendix
Check all parts for damage and wear.
Replace parts as necessary.
Check hose for holes and dry rot. Replace if
Go on to Sheet 3